Are your firestop submittals missing something for shafts? (part 2)
In our last blog post we talked a little about shaft walls, what they are made of and some things to keep an eye out for. We will build on that as we go.
Today we are going to look at firestop submittals as they relate to shaft wall assemblies, so the next time you are reviewing project documents you will have a better idea if something is missing. The easiest way to understand this discussion is to quickly review the UL nomenclature post found here so this will be easier to follow. If you do not know this nomenclature its much more difficult to conduct this exercise.
First let’s think about the RATED JOINTS. Let’s assume that the project has both block shafts and gypsum shafts. As you look at the firestop submittals pull out the HW (head of wall) details and look for the types of shaft walls you have on your project. For this discussion we will assume you have both gypsum and block shaft walls.
You will likely have a handful of HW details but if you have gypsum shafts you need to be sure the project has a detail for firestopping this gypsum shaft. When you look at the WL details for gypsum walls, you will notice it is not like the standard gypsum wall details, namely because the shaft walls are built differently so they need to be firestopped differently as well. This will require sealant at the shaft liner as well as on the outer layers of drywall. If you allow this wall type to be firestopped when the wall construction is complete, you will not have a compliant system because you will only have protection from one side of the wall. This would create a major liability for the installer as well as the GC, building owner and building occupants. If you are looking at a WL2000 series detail for plastic pipes, be sure to take a closer look, but do the same for all your penetration types.
If you have access to both sides of the wall, as you would in an elevator shaft, then it is easy to firestop the head of wall joint on a block wall from either side of the wall. Likewise you can firestop your through penetrations with either a CAJ or WJ detail. If you only have access to one side of the wall, you will need what is commonly referred to as a sandwiched detail and my guess is that it will likely be a WJ detail or possibly an engineering judgement. This would allow for firestop to be installed in four steps. Typically there would be installation of mineral wool recessed maybe 4-1/2” into the joint, then firestop sealant (let’s say it calls for ½” of sealant) then another layer of 3-1/2” of mineral wool followed by another ½” of sealant. There are 4 steps to this installation, which means 4 steps to any firestop inspection as well, unless the inspector wants to try to cut into this kind of joint application, which is going to be a challenge in and of itself. This also means that the firestop detail needs to show installation from one side if this is what the installers are doing.
That is what you expect to see when you are in the field, but when looking at the firestop submittals you need to be sure that the block wall detail that is provided can actually be installed on the project. Is it physically possible? You need to be sure there is a head of wall, bottom of wall and possibly a wall to wall detail for the gypsum assembly. It is not uncommon for a contractor to miss these details, so be on the lookout for them.
Next, think about what penetrations will be going through your shaft walls. The block and concrete walls often will not have access from the inside of the shaft so a sandwiched application needs to be used in many cases, though there are devices that can be used and installed from one side. If we are working on a project with you then we can help you determine which different manufacturers products would be best for various scenarios. Let’s say your stairwell walls are block or concrete. This means the firestop details you will need will start with either a CAJ or a WJ (potentially WK for thicker walls). You will need a 1000 series detail for your sprinkler pipes and conduits, unless you have plastic sprinkler pipes then you will need a 2000 series detail as well as a 3000 series for your MC cables. You won’t need a 7000 series detail for your ducts because they are going through a 2 hour wall and will require dampers. Pull out these details and be sure that if you only have one side access that the details will allow one sided access for the installation requirements. If not, you will need an Engineering Judgment. If you are in NJ, remember DCA does not allow EJ’s- sorry NJ.
Typically firestop installers will submit details for the various penetrations through a standard wall. These may be okay if the shaft wall type is included in what is allowed in the listed detail. If it is included, then you are fine, and if not then they need to submit a new detail. This will be found in item 1 of all details. These details will start with WL for gypsum framed walls and if it is a mechanical shaft you will likely have WL 1000 for metal pipes, WL 5000 for insulated pipes, maybe WL 2000 for plastic pipes. When doing the installation or inspection of these walls you will want to be sure to check annular space and sealant depth to be sure it conforms with the details. You will also want to be sure the installer firestops the shaft liner side before the outer two layers of drywall go up as you will see in one of the later posts.
We have given you a few things to be cautious about, but in our next post we will dig deeper into this and the building code. If you have questions about a recent firestop submittal please contact us for help.